SPG power generation system, providing optimum performance, reliability, and versatility for stationery standby, prime power, and continuous duty applications. All generator sets are prototype tested, factory build, and production tested.
ISO8528 - This generator set has been designed to meet ISO 8528 regulation.
ISO 9001 - This generator set is manufactured in facilities certified to ISO 9001.
This generator set is available with CE certification
Enclosed product is tested according to EU noise legislation 2000/14/EC
|Sound Attenuated Type|
|Voltage||Standby Rating (ESP)||Prime Rating (PRP)|
Standby Rating (ESP) : Continuous running at variable load for duration of an emergency. No overload is permitted on these ratings. In accordance with ISO 3046.
Prime Rating (PRP) : Continuous running at variable load for unlimited periods with 10% overload for 1 hour in any 12 hour period. In accordance with ISO 8528, ISO 3046.
|Engine Power Output at rated rpm||kWm||143.9|
|No. of Cylinders and Build||6 In Line|
|Aspiration and Cooling||Turbocharged and intercooled|
|Bore and Stroke||mm x mm||105x127|
|Fuel Consumption at full load||L/hr||33.1|
|Fuel Tank Capacity||Litre||320|
|Radiator Cooling Air||m³ /min.||281|
|Air Intake - Engine||m³ /min.||9.6|
|Exhaust Gas Flow||m³ /min.||24.4|
|Design||Brushless single bearing, revolving field/td>|
|Rotor||Single bearing, flexible disc|
|Insulation System||Class H|
|Standard Temperature Rise||125 - 163°C Continuous|
|Exciter type||Self Excited|
|Phase Rotation||A (U), B (V), C (W)|
|Alternator Cooling||Direct drive centrifugal blower fan|
|AC Waveform Total Harmonic Distortion||No load <1.5% Non distorting balanced linear load < 5%|
|Telephone Influence Factor (TUF)||<50 per NEMA MG-1-22.43|
|Telephone Harmonic Factor (THF)||<2%|
3/4 Pole Output Circuit Breaker
Transfer Switch 3 Pole
Transfer Switch 4 Pole
Earth Fault, single set
Bulk fuel tank
Automatic filling system
Fuel-water separator filter
Low fuel level alarm
Enclosure or sound proof canopy
Manual oil drain pump
Tool kit for maintenance
Control supervision and protection panel is mounted on the genset base frame. The control panel is equipped as follows: